Brass radiator valve
|Warranty:||2 Years||Model Number||XF50402 XF60258A|
|After-sale Service:||Online technical support||Type:||Floor Heating Systems|
|Brass ProjectSolution Capability:||graphic design,3D model design,total solution forProjects,CrossCategories Consolidation|
|Application:||House Apartment||Color:||Nickel plated|
|Place of Origin:||Zhejiang, China||MOQ:||1000|
|Brand Name:||SUNFLY||Keywords:||Temperature valve, white Handwheel|
|Product name:||Brass radiator valve|
Brass Hpb57-3（Accepting other copper materials with customer-specified, such as Hpb58-2,Hpb59-1,CW617N,CW603N and so on）
Raw Material, Forging,Roughcast,Slinging, CNC Machining,Inspection,Leaking Test, Assembly,Warehouse,Shipping
Material Testing,Raw Material Warehouse,Put In Material,Self-Inspection,First Inspection,Circle Inspection,Forging,Annealing,Self-Inspection,First Inspection,Circle Inspection,Machining, Self-Inspection,First Inspection,Circle Inspection,Finished Inspection,Semi-Finished Warehouse, Assembling,First Inspection,Circle Inspection,100% Seal Testing,Final Random Inspection, Finished Product Warehouse,Delivering
Radiator following,radiator accessories,heating accessories.
Main Export Markets
Europe,East-Europe,Russia,Middle-Asia,North America,South America and so on.
Manual regulation valve for controlling the fluid in the emitters of eating systems. These special valves can be converted from manual to thermostatic operation by simple replacement of the adjusting knob with a thermostatic control head. This means that the ambient temperature of any room in which they are installed can be constantly maintained at the set value. These valves have a special tailpiece with rubber hydraulic seal, permitting quick, safe onnection to the radiator without the use of additional sealing materials.
Case: Brass CW617N-UNI EN 12165
Stock: Brass CW614N-UNI EN 12164
Branch pipe: Brass CW614N-UNI EN 12164
Gaskets: EPDM peroxide
Application: Heating system
Maximum working pressure: 10 bar
Manual regulation valve rotates the handwheel to rotate the valve core, which plays the role of opening and closing.
The clockwise direction is off and the counterclockwise direction is on.
Manual regulation valve must be installed in horizontal position
Warnings: Manual regulation valve is installed incorrectly,two faults:
1) The presence of vibrations similar to hammer blows is caused by the fact that the
fluid passes through the valve in the direction opposite to that indicated by the arrow on the
body. To eliminate this malfunction, it is enough to restore the correct flow direction.
2) When the valve is opened / closed, the existence of noise is due to the high system
pressure difference. In order to solve this problem, it is recommended to install a variable
frequency water pump, a differential pressure regulator or a differential pressure bypass
valve at the same time.