Brass Air Vent valve
|After-sale Service:||Online technical support||Type:||Floor Heating parts|
|Brand Name:||SUNFLY||Color:||Nickel plated|
|Name:||Brass Air Vent valve||MOQ:||1000pcs|
|Place of Origin:||Zhejiang, China|
|Brass Project Solution Capability:||Graphic design, 3D model design, total solution for Projects, Cross Categories Consolidation|
Raw Material, Forging, Roughcast, Slinging, CNC Machining, Inspection, Leaking Test, Assembly, Warehouse, Shipping
Material Testing, Raw Material Warehouse, Put In Material, Self-Inspection, First Inspection, Circle Inspection, Forging, Annealing, Self-Inspection, First Inspection, Circle Inspection, Machining, Self-Inspection, First Inspection, Circle Inspection, Finished Inspection, Semi-Finished Warehouse, Assembling, First Inspection, Circle Inspection, 100% Seal Testing, Final Random Inspection, Finished Product Warehouse, Delivering
Air vent are used in independent heating systems, central heating systems, heating boilers, central air conditioning, floor heating and solar heating systems and other pipeline exhaust.
Main Export Markets
Europe,East-Europe,Russia,Middle-Asia,North America,South America and so on.
1. Purpose and scope
A float air vent is used to automatically remove air and other gases from pipelines and air collectors of internal systems (heating systems, cold and hot water supply, heat supply of ventilation units, air conditioners, collectors).
It protects closed piping systems from corrosion and cavitation and from the formation of air jams. The air vent can be used on pipelines transporting liquid media that are non-aggressive to the product materials (water, solutions of
propylene and ethylene glycols with a concentration of up to 40%).
The air vent is supplied to the consumer complete with a shut-off valve. The shut-off valve is used to connect the air vent to the system, and allows the installation and dismantling of the air vent without emptying the system.
2. The principle of operation of the air vent
In the absence of air, the air vent housing is filled with liquid, and the amendment keeps the exhaust valve closed. When air collects in the float chamber, the water level in it drops, and the float itself sinks to the bottom of the body.Then, using the lever-hinge mechanism, an exhaust valve opens through which air is vented to the atmosphere. After air outlet, water again fills the float chamber, raising corrections, which leads to the closure of the exhaust valve.Opening / closing cycles of the valve are repeated until air from the nearest part of the pipeline is free of air, having ceased to collect in the float chamber.